Siliphos Ball phosphorus crystal:
1.The formation of a fine corrosion protection film, to prevent the corrosion of the pipeline.
2. Prevent calcium, magnesium and other scale components in water adhere to the wall of the water pipe scale.
The usage method and input amount of silicon phosphorus crystal
A year's basic dose is initially allocated, followed by quarterly replacement of the missing dose.
Daily usage (ton) ×5~10ppm (concentration) ×365 days /1000= power-phos scheduled usage (kg)
Daily usage (ton) ×5~10ppm (concentration) ×90 days /1000= power-phos scheduled usage (kg)
Precautions for silicon and phosphorus crystals:
1. The inlet water temperature of the silicon and phosphorus crystal charging tank is < 30 ℃.
2. The silicon and phosphorus crystal charging tank should avoid heat source to prevent the temperature in the tank from being too high to dissolve the dissolved silicon and phosphorus crystal.
3, steam boiler water treatment, not applicable to silicon and phosphorus crystal equipment.
When the water system for silicon and phosphorus crystals is out of service for a long time, the silicon and phosphorus crystals should be removed from the charging tank and stored in a dry place after air drying
Application scope of silicon and phosphorus crystals:
1, widely used in hotels, restaurants, residential buildings, hospitals, schools, bath and sauna centers and factories of hot water circulation system or other water supply pipelines, can prevent scale, corrosion phenomenon, is "red water", "black water", "yellow water" and scale of the enemy.
We are here to help you! If you close the chatbox, you will automatically receive a responsefrom us via email. Please be sure to leave yourcontact details so that we can better assist